25%* Fill. Vertical and Horizontal. Type EYA: Female/Female. Type EYAM: Male/Female.
For Use with Threaded Rigid Metal Conduit and IMC.
– Class I, Division 1 and 2, Groups A, B, C, D
– Class II, Division 1 and 2, Groups E, F, G
– Class III
These O-Z/Gedney sealing fittings minimize the passage of gases and vapors and prevent the passage of flames from one portion of an electrical system to another through the conduit.
EYA & EYAM Series 25% Fill Vertical and Horizontal Conduit Sealing Fittings Catalog Page
* Per NEC 501.15(C)(6) seals in Class I, Division 1 and 2 must be limited to conductor fill of 25% of cross sectional area of a rigid metal conduit of the same trade size unless approved for higher percentage fill. See 40% fill sealing fittings.